Part B6 Rainwater services
VIC B6P7 Rainwater serviceNew for 2022
A rainwater service must—
- avoid the likelihood of contamination of water within the rainwater service, the cold water service, or the Network Utility Operator's drinking water supply (if connected); and
- not pose a hazard to public health; and
- not have an unprotected cross-connection with any Network Utility Operator's drinking water service.
VIC B6D2 General requirementsNew for 2022 (2019: Volume Two V2.6.1 and V13.12.0)
A rainwater service must comply with Section 15 of AS/NZS 3500.1.
The Victorian NCC 2019 rainwater tank variation (VIC V2.6.1 and V3.12.0 respectively) remains in effect until 30 September 2023 after which the following takes effect:
A rainwater tank must be installed in a Class 1 building in accordance with the regulations made under the Building Act 1993 (Victoria).
See Part B7 clause B7D4.