Part 3.12.4 Air movement
18.104.22.168 Air movement
the adjoining room is not a sanitary compartment; and
|Climate zone||Without a ceiling fan or evaporative cooler||With a ceiling fan||With an evaporative cooler|
|1||10%||7.5%||10% (see Note)|
|2||10%||7.5%||10% (see Note)|
|5||7.5%||5%||7.5% (see Note)|
|6, 7 and 8||As required by Part 3.8.5||As required by Part 3.8.5||As required by Part 3.8.5|
Note to Table 22.214.171.124: Because evaporative coolers are less effective than ceiling fans in more humid locations, the requirement for ventilation opening in climate zones 1, 2 and 5 with an evaporative cooler is the same as without one.
In humid locations, such as Darwin and Cairns, evaporative coolers would not provide the same cooling effect as in dryer climates. Although they would provide some benefit from the air movement if operated in a “fan-only” mode, they would cause discomfort, possible condensation and possible mould growth if operated in an evaporative “water-on” mode. However, even though a concession is not given in climate zones 1, 2 and 5, there are locations, particularly in climate zone 5, where evaporative coolers would be effective.
126.96.36.199 Ventilation openings
pass through not more than two openings in the internal walls with each opening having an area of not less than 1.5 m2; and
have a distance along the breeze path between ventilation openings of not more than 20 m.
- Ventilation openings should be designed to allow the interior of the building to take full advantage of any natural breeze. Careful consideration should be given to the type and location of openings to ensure optimum effect is achieved and that internal “dead air pockets” are avoided.
- An opening may serve more than one breeze path.
- Two openings are stated in (b)(i) as the limit of the number of openings permitted in a breeze path. These are typically doorways. Larger openings, such as those between adjoining lounge and dining areas in the same space are unlikely to restrict air movement significantly.
188.8.131.52 Ceiling fans and evaporative coolers
be permanently installed; and
have a speed controller; and
for ceiling fans, serve the whole room, with the floor area that a single fan serves not exceeding—
15 m2 if it has a blade rotation diameter of greater than or equal to 900 mm; and
25 m2 if it has a blade rotation diameter of greater than or equal to 1200 mm.